This article was originally published in the September/October 1996 issue of Home Energy Magazine. Some formatting inconsistencies may be evident in older archive content.
| Back to Contents Page | Home Energy Index | About Home Energy |
Home Energy Magazine Online September/October 1996
Submetering I: No Guessing with Gas
In the past, submetering home gas appliances has been awkward and expensive. Now the Tokyo Gas Company is testing a new method to gather individual gas appliance consumption data in Tokyo homes. The method does not require expensive equipment or intrusive installations. Instead, it relies on relatively simple hardware and very sophisticated computer algorithms.
There are three conventional approaches to estimating energy use of individual gas appliances. The first is to put a gas meter on each gas appliance in each home. This technique is expensive, making it difficult to monitor a statistically representative sample of homes. Also, energy auditors and residents are reluctant to have gas lines cut into. As a result, most studies monitor selected appliances in a few homes and settle for typical values, rather than a true average.
In other studies, researchers have inserted thermal sensors in the major combustion appliances and measured elapsed time to calculate consumption. Although this technique is much cheaper than direct metering of gas use, there is greater uncertainty about actual consumption.
The third traditional technique uses monthly gas billing data for a large number of homes combined with details of the appliances present in each home. These conditional demand studies reconcile variations in appliance ownership with differences in energy use. Such studies have been undertaken both in Japan and in the United States. But when there is little variation in appliance ownership from one house to another (as in many parts of Japan), the results are susceptible to large uncertainties.Disaggregation Without Aggravation The new monitoring system relies on innovations in both hardware and software. The hardware is a sensitive whole-house gas meter connected to a data logging system. The software consists of a set of algorithms that break down the whole-house consumption into each appliance's consumption. Similar methods are being developed for nonintrusive electrical metering (see Submetering II: In the Know with Electrical Flow, p.7).
Figure 1 shows the configuration of the Japanese metering system. A mechanical meter sends an electronic pulse every time 0.0318 ft3 (0.9 liter) of gas has flowed. Each meter is equipped with a data logger that time-stamps each pulse and thus records the elapsed time between consecutive pulses. When more gas is being used, the pulses occur more rapidly.
Each day, the logger records tens to thousands of pulses, depending on the amount of gas appliance activity. Periodically, data collectors download the list of time stamps. For the Tokyo study, we collected data from each customer site four times a year at most; downloading each logger took only a few seconds.
Estimation of end uses consists of two steps: decomposition and identification. In the decomposition step, the computer notices changes in gas use. By assuming that only one appliance is being turned on at a time, the computer can keep track of how many appliances are operating, and at what flow rates. When there is a significant increase or decrease in gas flow, we assume that one appliance has been turned on or off. The computer keeps track of the number of active appliances, and of gas consumption by each one.
The identification step combines audit information and the decomposed consumption data. When we install the meters, we record what gas appliances a house has, and their rated capacities. Using this information, the computer matches appliances with the flow rate and duration of gas use. Table 1 lists typical Japanese gas appliances, their rated input, and the elapsed time (in seconds) between pulses at the rated consumption.
We installed 20 of the data loggers in utility employees' houses and apartments to test the hardware and procedures. Then we compared the estimates with data obtained through an interview. Examination with the logged data from the different samples showed at least 95% accuracy in estimation.
The algorithms can still be confused by some relatively common situations. For example, in Japan, many space heaters have continuously variable combustion, with more gas flowing when the heating load is greater. If a window is opened when a heater is operating, the heater's gas flow changes from low to high, making the algorithm think another appliance has turned on. Improved algorithms should allow identification of variable-rate gas appliances.
Nevertheless, the system was judged sufficiently accurate to broaden the study. By the end of 1996, over 900 homes in the Tokyo area will have been monitored with the nonintrusive technique.
Although the nonintrusive monitoring system has worked well in Japanese homes, there are several differences in the way gas is used in North America. For instance, American appliances often have pilot lights, which are rare in Japan. While the algorithms could be easily adjusted to account for the constant load created by pilot lights, they will not be able to determine the amount of energy consumed by each appliance's pilot. This may require additional measurements during the audit. American homes also typically have more gas appliances than Japanese homes: clothes dryers, decorative fireplaces, pool and spa heaters, and exterior radiant heating elements are all more common in North America. This makes disaggregation more complicated, and computing requirements increase substantially. Finally, American appliances are more likely to have variable combustion rates, which can mislead the computer. However, none of these appears to be an insurmountable obstacle.
Nonintrusive submetering has already given us new insights into customer behavior. For example, we now know that family size and number of faucets in a home are much more accurate predictors of water heating energy use than the type of water heater. The data have also helped the gas utility to determine the variables affecting the demand for gas in Japanese homes. This permits more efficient operation of the supply and distribution system and more accurate demand forecasting. In addition, the impacts of fuel switching, retrofits, and behavioral changes can now be easily observed.
-Shin Yamagami and Hajime NakamuraShin Yamagami is a senior manager and Hajime Nakamura a researcher at the Tokyo Gas Company, Limited, in Tokyo, Japan.
For more information, see Yamagami, Shin, Hajime Nakamura, and Alan Meier. Nonintrusive Submonitoring of Residential Gas Appliances. In Proceedings, ACEEE 1996 Summer Study on Energy Efficiency in Buildings. Washington, D.C.: ACEEE, 1996.
| Back to Contents Page | Home Energy Index | About Home Energy |
Home Energy can be reached at: email@example.com
- FIRST PAGE
- PREVIOUS PAGE