This article was originally published in the September/October 1997 issue of Home Energy Magazine. Some formatting inconsistencies may be evident in older archive content.
| Back to Contents Page | Home Energy Index | About Home Energy |
Home Energy Magazine Online September/October 1997
What's Being Built Out There?
Is 3% a Pie in the Sky?
At Advanced Energy, we train installers on behalf of utilities across the nation. In North Carolina, Carolina Power and Light adopted the standard of a national program called E-Seal. E-Seal won't certify a home if total duct leakage, expressed in ft3 per minute with the house depressurized to 50 Pascals (CFM50), exceeds 8% of the conditioned floor area. This is the equivalent of 5% tested at 25 Pa.
North Carolina's Duke Power and North Carolina Power have even more stringent programs. They require that total duct leakage in CFM25 not exceed 3% of the conditioned floor area. That is, a 1,000 ft2 house's total duct leakage cannot exceed 30 CFM25.
All of these standards are far below the 20% leakage in CFM25 we found in our survey. When reality is so different from a standard, it's reasonable to ask whether the standard is realistic.
Since 1993, NC Power's new construction program has sponsored several training workshops. Led by AE, workshops teach HVAC installers the hows and whys of fabricating airtight air distribution systems. NC Power regularly tests duct air-tightness to determine if the ducts meet the standard.
The performance testing contractor, Grady Lassiter, provides additional hands-on time with any crew that doesn't meet the standard, showing them how to find and fix the problems, explaining why it's important, and working to get them excited about doing quality work. He also shows them how to cover and seal the boots, which serves two purposes--it keeps soda cans, half-eaten Big Macs, and other construction debris out of the ducts, and speeds up his testing process in future houses.
During 1993-94, Lassiter tested 171 systems. Forty-nine (29%) had more than 3% leakage, requiring a retest. Sixty-one (36%) had leakage of 1% or less on the first test. Mean leakage was 3% and the range was 0-20%. That is, some contractors actually achieved an airtight duct system and the very worst was equal to the median we found in typical new construction.
In 1995, Lassiter tested 170 systems and found only 6 (3.5%) with more than the 3% standard, and 82 (48%) with 1% leakage or less. The mean was 1.75%, and the range was 0 to 6%.
This clearly demonstrates that the 3% standard is attainable by typical crews who have the proper training, and who carry out the necessary follow-up and performance testing.
|A blower door used for pressure testing is visible in this home from the Advanced Energy study.|
The five main concerns about tightness are that:
- Air leakage (infiltration/exfiltration) accounts for up to 40% of the heating and cooling bills of most houses.
- Air leakage causes substantial comfort problems.
- Air leakage is responsible for maintenance and durability problems, due to moisture being carried in on air.
- Air leakage causes some indoor air quality (IAQ) problems, due to pollutants being carried in on air.
- Airtightness may reduce indoor air pollutant dilution and cause IAQ and moisture problems.
|Figure 1. Distribution of homes at different leakage rates, as determined from blower door tests.|
Only 3 houses out of 51 (6%) met our whole-house air sealing target. The median house was about 50% leakier than our recommended rate. Based on this sample, it is safe to say that typical new houses in the Carolinas have a long way to go before we would consider them tight enough with respect to energy efficiency, comfort, and IAQ.
On the other hand, they may be too tight to count on natural ventilation. ASHRAE recommends that homes with estimated natural infiltration rates of less than 0.35 ACH should have mechanical ventilation. Nineteen out of 100 houses--nearly 20%--fell into this range. Our methodology for estimating natural infiltration, however, may have overestimated infiltration. Tracer gas testing of 23 homes indicated that a much higher percentage are below 0.35 ACH. If this outcome is supported by more extensive testing, it would suggest that substantially more houses may need mechanical ventilation. Only one of the 100 houses had a whole-house ventilation system.
In our part of the country, even houses with estimated 0.35 ACH or higher may not get adequate natural fresh air during much of the year. Actual air leakage depends upon driving forces, such as wind, so there can be significant periods when even a very leaky home does not get enough fresh-air ventilation for occupant health or moisture control.
Thus ventilation often depends on the bathroom fan--a bath fan was present in all of the houses we visited. Typical bath fans make noise, and they may or may not move air out of the house. Most of the fans in the study were actually vented to the outside, but several simply terminated in the attic, breaking code and risking moisture problems, but saving construction time and cost. Among those which did vent to the outside, circuitous duct paths guaranteed reduced air flow.
|Arnie Katz of Advanced Energy (center) and two members of the North Carolina Housing Finance Agency examine insulation they are using in a new home construction project for Habitat for Humanity.|
We came upon several instances of catastrophic duct failure--ducts that were totally disconnected. We found this condition in both attics and crawlspaces. In one case, a homeowner told us she had complained about lack of heating and cooling to the master bedroom for nearly a year. Each time she called the contractor sent someone out, found no problems, and determined that the system was working fine.
While checking crawlspace insulation, we found a supply duct lying on the ground under the master bedroom. The bedroom was in the far corner of the house, far from the crawlspace access door. With major ductwork between the access door and the dead duct, the only way to find the disconnection was to slither on the ground like a snake, with barely enough clearance to get under the main trunk line. As every energy auditor knows, these are usually the places where trouble is found.
In another house, we found a 50-ft run of 8-inch flex duct. It started at the air handler in one attic, wound under a window seat into another attic, and stopped, wide open, directly under a gable end vent. The decision not to condition the walk-in closet under the duct termination was never translated into removing the duct. While it certainly created one of the most comfortable attics I've ever been in, this wasn't helping the homeowner's energy bill. On the other hand, adding the attic and, indeed, the entire outside world, to the load of the house probably brought the equipment size closer to the actual load, given the oversizing we found.
In general, we found duct installation that fell short of local utility standards. Installers still don't seal duct systems. When they do seal, it is too often with substandard duct tape. Though mastic is appearing more and more, it is still the exception rather than the rule.
Our survey measured total leakage on 130 duct systems in 96 houses. The median measured duct leakage was 261 CFM25 per system and 360 CFM25 per house total. Expressed as a percentage of conditioned floor area, systems had a median leakage of 19.5%, ranging from 4% to 79%. This compared poorly with our standard, and with the standard set by E-Seal, a national energy efficiency program sponsored by the Edison Electric Institute. No systems met our standard of 3%, and only three met the E-Seal standard of 5%. Thirteen systems had more than 30% leakage. The median leakage is over six times the Duke Power and NC Power standard, and almost four times the E-Seal standard. Duct leakage is clearly still a major problem in new homes.
|Figure 2. Distribution of homes at different natural air change rates, converted from blower door leakage data.|
When these homes were built, the North Carolina Building Code required R-30 attics. Based on our admittedly rough methodology, we estimate that 23% of the homes have attic insulation levels clearly below R-30. Based on other recent studies, it's quite possible that had we done more extensive testing, such as cookie cutter tests (see A Plan to Stop Fluffing and Cheating in Attic Insulation HE, May/June '96, p. 10), we would have found even more homes with attic insulation below R-30. One house was insulated only by a 2-inch dusting of loose-fill insulation over about a quarter of the ceiling.
We also noted the nominal R-value of floor insulation above crawlspaces or basements, but we didn't try to quantify actual R-values. While all the houses had the code-mandated R-19 insulation installed, the field staff frequently mentioned that the effective R-value was compromised by poor to mediocre installation. Typically installed with tiger teeth supports, the insulation was usually highly compressed in the middle and had gaps along the joists. It was stuffed behind pipes, wires, cross-bridging, and other framing members, and in some cases was already falling down at the time of our survey.
The other oft-noted problem was a lack of solid sheathing material on the attic side of kneewalls. We recommend sheathing to keep 140°F attic air from circulating through the insulation. In several cases, we noted kneewall insulation that had already fallen out of the cavities.
|Figure 3. Distribution of homes with undersized, correctly sized, and oversized heat pumps.|
We measured the charge in 22 systems in 13 homes. Of these 22 systems, 14 were overcharged, 5 were undercharged, and only 3 were correctly charged.Heat Pump and Central Air Conditioner Sizing HVAC contractors clearly still believe that bigger is better. Considering the duct leakage and the overcharging found in the survey, oversizing may in fact be necessary to maintain comfortable cooling levels. But the price for the homeowner is high.
We ran load calculations on 50 houses (59 systems) with heat pumps using Elite Software's RHVAC program. The program calculates loads based on Manual J. The recommended practice down here in the mold belt of the United States is to size heat pumps based on the cooling load and make up any difference in the heating load with electric resistance strip heaters.
We compared the Manual J cooling load with the actual cooling capacity of the unit installed in each house and used ACCA Manual S to determine proper sizing guidelines. Specifically, Manual S says, If heat pump equipment (air-source or water-source) is installed in a warm climate or moderate climate, the total cooling capacity should not exceed the total cooling load by more than 15 percent.
Unfortunately, out of 59 heat pumps, only 6 lived up to this standard. One was undersized. The remaining 52 units, or 88% of the heat pumps, were oversized. Median oversizing was 0.81 tons, with the most oversized unit rated to provide an extra 2.3 tons of cooling. Oversized air conditioning equipment tends to be noisy and suffers from short-cycling. Short-cycling can cause moisture buildup and a major loss of efficiency (see Bigger Is Not Better: Sizing Air Conditioners Properly, HE May/June '95, p.19).
|Duct hunting season.|
Each of these problems can be substantially improved or eliminated at relatively modest cost, using proven techniques and equipment. This is not, after all, rocket science. It's simply building science.
| Home Energy Home Page | Back Issues of Home Energy |
Home Energy can be reached at: firstname.lastname@example.org
Home Energy magazine -- Please read our Copyright Notice
- FIRST PAGE
- PREVIOUS PAGE